How do you replace old copper pipes and fittings without knowing how to solder?
More importantly, can you do this without having a ton of money, time, or plumbing experience?
These questions came to me after noticing an old corroding copper shutoff valve in our basement ceiling. In the past I’ve paid plumbers a decent amount of money ($90 to $160) to replace one foot sections of copper pipe.
You can easily repair copper pipes and shutoff valves with the greatest plumbing supply ever: SharBite push fit pipe connectors.
I’ve used SharkBite products in several rental homes as well as my own personal house with no issues. A beginner at plumbing can use SharkBite pipe connectors and can eliminate the use of a plumbing contractor for basic repairs. I love my plumbers but if I can save a little money for my daughter’s college fund then I’m gonna do it.
If you know how to use a measuring tape, sharpie marker, and copper pipe cutter (which these days my 10 year can manhandle) you can do this project.
Here are the supplies you’ll need:
- SharkBite shutoff valve ($11.05)
- SharkBite Slip End Fitting ($12.24)
- AutoCut copper pipe cutter ($24.00)
- Sharpie marker ($0.97)
- Measuring tape ($9.88)
- Extra copper pipe ($7.92)
The total cost for the SharkBite pipe connectors, AutoCut tool, and extra copper pipe is $55.22. Yes, it’s a bit expensive but you’ll save a ton of money doing these types of plumbing projects yourself.
And the kicker is this project takes all of 10 minutes.
I guarantee this is an easy task and you’ll be super happy with the results. If you don’t have time to do anything else you should watch the video because it shows you just how easy SharkBite fittings are to use.
So let’s get to it!
Removing the Old Shutoff Valve,Pipes, & Fittings
First, shutoff the water to your house at the water main then drain the water from the lowest point.
In my case I drained all the water from the pipes by turning on the water in the laundry tub. You’ll only need to do this for the cold water if the pipe you’re working on supplies the exterior of your home. You shouldn’t have warm water running to the exterior of your house.
You’ll want to grab a container that can collect the excess water that comes from the pipe you’re cutting.
SharkBite fittings need 1 inch of pipe to make a good connection. Keep this in mind when cutting out the old pipes and fittings.
The old corroded shutoff valve that needed to be replaced was in our basement ceiling between two joists. Even though I only needed 1 inch for the new SharkBite valve I measured 1 1/2 inches away from the joist to give some extra cushion. You can make a mark with a sharpie to indicate where you’d like to cut the copper pipe.
Use the AutoCut copper tubing cutter to make the first cut in the old copper pipe. I LOVE this tool because all you need to do is snap it onto the old pipe, close the gate, and rotate until the cut is complete.
I bought this at Lowes but you an find it at http://www.drainbrain.com.
Water will come out of the first cut in the old pipe and you’ll need to collect it in a small container.
Now it’s time to measure where the second cut needs to go.
In order to connect the new SharkBite shutoff valve to the old copper pipe you’ll need to use a SharkBite Slip End fitting. This pipe connector is different than a traditional SharkBite in that you’ll be able to slide the copper pipe into it by up to 3 inches. This is super useful when you need to replace pipes and connectors in the middle of a copper line run.
Remember that in my case the old shutoff valve was sandwiched between two joists. I measured 1 1/2 inches away from the joist for the first cut.
For the second cut, I measured and made a mark 3 1/2 inches away from the second joist just left of the old valve. This ensured there would be plenty of room for the Slip End fitting.
Cut the copper pipe at this second mark using the AutoCut tool.
With the old shutoff valve and pipe removed it’s time to use the SharkBites!!!
[ois skin=”Duplicate of HRT Video Newsletter-Bottom of Post”]
Using the Greatest Plumbing Supply Ever: SharkBite Push Fit Pipe Connectors
Spot the end of the first cut you made and measure in 1 inch.
Make a mark with the sharpie.
Push the SharkBite shutoff valve onto the copper pipe until it fits snug and flush with the 1 inch sharpie mark.
BAM!! You connected a shutoff valve in less than 1 minute.
The valve will rotate freely so don’t be alarmed or concerned that it isn’t properly installed.
Now it’s time to push on the Slip End fitting.
Look at the second cut you made in the copper pipe and measure in 1 inch.
Again, make a mark with the sharpie.
Push the Slip End fitting onto the copper pipe until it meets up with the sharpie mark.
Now measure the distance between the the Slip End fitting and the shutoff valve. Add 2 inches to this measurement. This is the total length of copper pipe you need.
Watch this video to see just how easy this entire process is for even the very beginner beginner (and no this isn’t a typo).
[tubepress video = “sEsqtSA7HsM”]
So that’s it. Now you know how to use SharkBite fittings to replace copper pipes and shutoff valves.
All of the supplies I used are for 1/2 inch copper pipe. My plumber recommends using Type L copper because it has a thicker wall than Type M. You can see the type by looking on the side of the copper pipe.
Do you have a fear of working on your own plumbing? Is there a simple plumbing project you’d like to do but don’t want to start?
Share your thoughts below in the comment section. If you’ve had a great experience with SharkBite fittings please let me know that as well by leaving a comment.
As usual, THANK YOU so much for visiting Home Repair Tutor. Your time is precious and I really appreciate your support by dropping in today. My goal is to help you with your weekend projects so that your house is a bit closer to being modernized, clean, and safe.
Make it a great day.
P.S. One of my fans pointed something out: if your pipes are properly grounded the SharkBite will break that grounding effect. You’ll have to add a copper jumper cable. Attach the jumper cable to the copper pipes on the left and the right of the SharkBite fitting with clamps to ensure the pipe is re-grounded. Thanks Scott for pointing this out!!!
P.P.S. Do you like inspiring pictures of kitchens & bathrooms that get your creative juices flowing? Follow me on Pinterest and view my Boards. I put them together for the Home Repair Tutor fans and constantly add new pins. Click on this Pinterest button then Follow the Board you like. I guarantee you’ll find some really fantastic ideas.
You can also connect with Me on Google+ by Clicking on this link . I like to share pictures, tips, and other random entertaining stuff. So don’t be shy, add me to your Circle